This content is not included in your SAE MOBILUS subscription, or you are not logged in.
Recent Experiences with Iodine Water Disinfection in Shuttle
ISSN: 0148-7191, e-ISSN: 2688-3627
Published July 01, 1990 by SAE International in United States
Annotation ability available
Microbial proliferation in the STS potable water system is prevented by maintaining a 2-5 ppm iodine residual. The iodine is added to fuel cell water by an iodinated ion exchange resin in the Microbial Check Valve (MCV). Crew comments indicated excessive iodine in the potable water. To better define the problem, a method of in-flight iodine analysis was developed. Inflight analysis during STS-30 and STS-28 indicated iodine residuals were generally in the 9-13 ppm range. It was determined that the high iodine residual was caused by MCV influent temperatures in excess of 120 °F. This is well above the MCV operating range of 65-90 °F. The solution to this problem was to develop a resin suitable for the higher temperatures. Since 8 months were required to formulate a MCV resin suitable for the higher temperatures, a temporary solution was necessary. Two additional MCV's were installed on the chilled and ambient water lines leading into the galley to remove the excess iodine. These reduced the iodine residual to 3-4 ppm during STS-33, STS-34, STS-36 and STS-32. A high-temperature resin was formulated and was initially flown on STS-31.
CitationGibbons, R., Flanagan, D., Schultz, J., Sauer, R. et al., "Recent Experiences with Iodine Water Disinfection in Shuttle," SAE Technical Paper 901356, 1990, https://doi.org/10.4271/901356.
- Columbo, G.V., Putnam, D.F. and Sauer, R.L. “Microbial Check Valve for Shuttle” ASME Paper 78-ENAs-27, July 1978.
- Iodinated Resin Specifications for 2 ppm Residual Resin, Rev. A. Umpqua Research Company, CPS100, November 1978.
- Standard Methods for the Examination of Water and Wastewater, 17th Edition, American Public Health Association, 1989.
- Sauer, R.L. and Westover, J.B. “The Potable Water System In Skylab” 4th Intersociety Conference on Environmental Systems, ASME Paper 74-ENAs-17, July 1974.
- Lambert, J.L. “Linear Starch Reagents” Analytical Chemistry, Vol 23, p. 1247, September 1951.
- Lambert, J.L., Fina, G.T. and Dikeman, E.F. “Quickly Dissolving Amylose Indicator in Cadmium Iodide-Linear Starch Colorimetric Reagent” Analytical Chemistry, Vol 54, p. 828, 1982.
- Lambert, J.L. and Rhoads, S.C. “Preparation of Linear Potato Starch Fraction for Quantitative Colorimetric Iodimetry” Analytical Chemistry, Vol 28, p. 1629, October 1956.
- Allen, T.L. and Keefer, R.M.; “The Formation of Hypoiodous Acid and Hydrated Iodine Cation by the Hydrolysis of Iodine” Journal of the American Chemical Society, Vol. 77, p. 2957, June 1955.
- Jolly, C.D. “High Temperature Microbial Check Valve Resin Development” Umpqua Research Co. URC No. 91019-1, February 1990.
- Iodinated Resin Certification (High Temperature Resin), Umpqua Research Company Standard Procedures, No. SP309, December, 1989.