Thermal Comfort Simulation for Manufacturing Plants
Published April 2, 2019 by SAE International in United States
Downloadable datasets for this paper availableAnnotation of this paper is available
Manufacturing processes often produce a large amount of heat, which needs to be pumped out of the factory to maintain thermal stability and comfort. Thermal comfort is essential to maintain a suitable working environment in a factory. It has a strong impact on the health and productivity of workers. In addition, it is mandatory to keep the working environment within specified thermal and relative humidity ranges. Periodic assessments of these thermal parameters is routine in most factories. Inclusion of additional manufacturing equipment or processes can lead to a significant change in the working environment and consequent comfort, this needs to be addressed quickly. Rather than wait to measure these effects it is preferable to develop a reliable simulation method for the proactive study and improvement of thermal comfort levels. A reliable simulation approach is developed in this study for the prediction of thermal comfort in an automotive manufacturing plant. Computational fluid dynamics (CFD) models along with on-site measurement data are used in this study to predict temperature distribution across the factory floor. Rectangular machine bounding boxes with an average measured temperature are used to represent individual machines. Further, the solar load with respect to plant location and roof thermal insulation have been considered in this study. The simulation approach presented correlates well with the measurements made as part of this study. This underscores the predictive validity of the approach.
CitationS, S., Palani, S., Fei, D., Srinivasan, B. et al., "Thermal Comfort Simulation for Manufacturing Plants," SAE Technical Paper 2019-01-0899, 2019, https://doi.org/10.4271/2019-01-0899.
Data Sets - Support Documents
|[Unnamed Dataset 1]|
- American Society of Heating, “Refrigerating and Air Condition Engineers,” ANSI/ASHRAE Standard 55-2004, ASHRAE, Atlanta, GA, 2004.
- Fang, L., Clausen, G., and Fanger, P.O., “Impact of Temperature and Humidity on the Perception of Indoor Air Quality,” Indoor Air 8(2):80-90, 1998, doi:10.1111/j.1600-0668.1998.t01-2-00003.x.
- Kolarik, J., Toftum, J., Olesen, B.W., and Shitzer, A., “Occupant Responses and Office Work Performance in Environments with Moderately Drifting Operative Temperatures (RP-1269),” HVAC & R Research 15(5):931-960, 2009.
- Chen, Q. and Zhai, Z., “The Use of CFD Tools for Indoor Environmental Design,” . In: Malkawi, Augenbroe G., editors. Advanced Building Simulation Book. First Edition. (New York, Spon Press, 2004), 119-140.
- Carrilho da Graca, G., Martins, N.R., and Horta, C.S., “Thermal and Airflow Simulation of a Naturally Ventilated Shopping Mall,” Energy and Buildings 50:177-188, 2012, doi:10.1016/j.enbuild.2012.03.037.
- Nielsen, P.V., “Fifty Years of CFD for Room Air Distribution,” Building and Environment 91:78-90, 2015, doi:10.1016/j.buildenv.2015.02.035.
- Zhang, J., Long, Z., Liu, W., and Chen, Q., “Strategy for Studying Ventilation Performance in Factories,” Aerosol and Air Quality Research 16:442-452, 2016, doi:10.4209/aaqr.2014.09.0210.
- Mohamed, S. and Srinavin, K., “Thermal Environment Effects on Construction Workers’ Productivity,” Work Study 51(6):297-302, 2002, doi:10.1108/00438020210441849.
- Star-CCM+ Manual, Version 13.02.