Monitoring Energy Consumption at the Canada Centre ATES Site
Published August 3, 1992 by SAE International in United States
Annotation of this paper is available
The Canada Centre Building was designed to accommodate 1,900 workers on 12 floors in a 30,000 m2 office structure in Scarborough, Canada. Its unique energy conserving features include 700 m2 of roof mounted solar energy collectors, chillers modified to operate as heat pumps, and an aquifer thermal energy storage (ATES) system operating on four 60 m deep wells producing flows of 10 to 30 L/s from a 10 m thick fine to medium sand aquifer. The ATES and solar domestic hot water heating systems have been used since 1985.
Instrumentation for ATES performance monitoring was installed during construction of the building, for research and verification of geothermal models. Energy monitoring, however, was implemented in 1991, to evaluate the energy consumed in operating various energy conserving systems. Initial data show coefficients of performance (COP) of about 4 to 5 for the ATES and heat pump systems respectively.
CitationMorofsky, E., Cataford, R., and Mirza, C., "Monitoring Energy Consumption at the Canada Centre ATES Site," SAE Technical Paper 929198, 1992, https://doi.org/10.4271/929198.
- Hickling Corporation. 1990. Canada Centre Building, Scarborough - Five Year Energy Systems Performance Summary. Hickling Ref. 2720. Prepared for IEA ECES Annex 7 Working Group. April.
- Mirza, C., Lau, K. C., Nadon, R. L. and Crawford, A. M. 1985. Aquifer thermal energy storage - a new technology. Proceedings, Seventh Canadian Hydrotechnical Conference, Saskatoon, Sask. May, vol. 1A, pp: 389-409.
- Morofsky, E. L. 1983. Overview of Canadian aquifer thermal energy storage field trials. Proceedings, International Conference on Heat Storage in Theory and Practice, Stockholm, Sweden. Swedish Council for Building Research, pp:221-231
- Strata Engineering Corp. 1992. Well Efficiency Testing, Aquifer Thermal Energy Storage System, Canada Centre Building, Scarborough. Report S-92-331 submitted to Public Works Canada, Ontario Region, April.