This content is not included in your SAE MOBILUS subscription, or you are not logged in.
Gas Turbines and Dust - The Effectiveness of an Inlet Air Cleaner
ISSN: 0148-7191, e-ISSN: 2688-3627
Published February 01, 1970 by SAE International in United States
Annotation ability available
Two 60 kw, gas-turbine powered generator sets were operated together in a controlled environment containing 0.005 gm of selected dust per cubic foot of ambient air. One of the sets was equipped with an inertial-type air cleaner, but the other was unprotected.
The unprotected set was unable to carry its rated 60 kw load after 6 hr and 50 min of operation; the unit equipped with the intake air cleaner carried its rated load for nearly 132 hr before automatic shutdown occurred.
Both turbines were disassembled and inspected after shutdown. Most of the damage was confined to the air inlet housings, diffuser vanes, and turbine nozzles. Damage and dust ingestion parameters are discussed.
CitationLawrason, G., "Gas Turbines and Dust - The Effectiveness of an Inlet Air Cleaner," SAE Technical Paper 700704, 1970, https://doi.org/10.4271/700704.
- Montgomery James E. and Clark J. M. Jr., “Dust Erosion Parameters for a Gas Turbine”. Paper 538A, presented at SAE Summer Meeting, Atlantic City, June 1962.
- Engelhardt R. W., and Knebel G. W., “Characteristics of the Dust Environment in the Vicinity of Military Activities.” Southwest Research Institute Report No. AR-642, January 1968.*
- Pearson R. O. and Meriwether R. F., “Effects of Dust Ingestion on Gas Turbine Performance and Endurance.” Southwest Research Institute Report No. AR-455, March 26, 1962.*
- Wood C. D. and Espenschade P. W., “Mechanisms of Dust Erosion.” SAE Transactions, Vol. 73 (1964), paper 880-A.
- Thomas Gary E., “Effectiveness of an Inertial Air Cleaner in Extending Gas Turbine Life in a Dusty Environment.” Southwest Research Institute Report No. AR-643, March 1968.*